- Hot search：
AWS C4.3/C4.3M:2018 pdf free download
AWS C4.3/C4.3M:2018 pdf free download.Recommended Practices for Oxyfuel Gias Heating Torch Operation.
Cylinders shall not be placed where they might become part of an electrical circuit. Cylinders shall be kept away from anything that can be used for grounding electrical circuits. Poor grounding during arc welding could result in arcing to the cylinder, which could cause weakening of the cylinder walls and possible rupture. An arc shall never be struck on any gas cylinder.
Never completely drain any cylinder or leave the valve open on “emp1y cylinders. This could result in contamination of the cylinder.
4.11.2 handling. Any action that can cause cylinders to be damaged by impact should be avoided. Bcforc moving thc cylinders, the regulators shall be removed and the protective caps installed, except when moved on a cylinder cart designed for gas cylinders. Slings or magnets shall ncver be used to move cylinders. Cylinders shall not be lifted by the cap. Cylinders shall never be used as a support or roller of any kind.
If any cylinder is damaged or found to be defective in any way. it shall be removed from service immediately. The supplier shall be notified and the cylinder returned with a tag stating the problem. If a cylinder is leaking. it shall be immediately removed to a safe outside location. The supplier shall be notified, and their instructions followed.
Under no circumstances shall anyone try to fill one cylinder from another. This operation is extremely hazardous and can result in an explosion or cylinder rupture resulting in personal injury.
4.11.3 Safe Storage. Valves shall be closed and caps replaced on all cylinders that are empty or not in use. Oxygen and fuel gas cylinders shall always he segregated during storage. Empty cylinders should be marked accordingly and segregated from full cylinders. Unused gas should no, be released from cylinders.
Container storage area.s shall be posted with the name of the gas and ‘No Smoking” restrictions. Adequate spacing between oxygen and fuel gas storage areas must be provided unless a fire-rated harrier is installed between the two Isee OSI-IA and other local regulations). In seismic areas special restraints may be necessary to prevent the cylinders from falling over. Cylinders should be stored in a properly nested configuration with three points of contact between a cylinder and other cylinders or a wall. This nesting concept applies to outside or end cylinders in the nest.
4.12 Safe Working Environment. Oxyfuel gas heating equipment should he operated only in areas free of conditions or materials that could be hazardous to the operator or others. The following is a summary of some important considerations:
(I) I)o not use lighted torches where chlorinated hydrocarbon solvent vapors are present. Exposure of such vapors to heat may result in the formation of phosgene (an extremely poisonous gas). AWS C4.3/C4.3M:2018 pdf free download.
All resources on this website are from the Internet. It is only for personal study and research. No one is allowed to use it for any commercial purpose. If you need, please buy the genuine standard. If there is any infringement of your copyright, please contact the webmaster in time, and I will correct it immediately.
- Maybe you like
- Latest Updates
- ISO 287-2009 pdf free download
- ISO 527-5-2009 pdf free download
- ISO 659-2009 pdf free download
- ISO 660-2009 pdf free download
- ISO 712-2009 pdf free download
- ISO 725-2009 pdf free download
- ISO 730-2009 pdf free download
- ISO 927-2009 pdf free download
- ISO 2041-2009 pdf free download
- ISO 3040-2009 pdf free download
- ISO 3506-2-2009 pdf free download
- ISO 3506-3-2009 pdf free download