- Hot search：
CSA B139-09 pdf free download
CSA B139-09 pdf free download.Installation code for oil-burning equipment.
When two or more appliances are connected to the same vent,
(a) the appliances shall be oil- or gas-fired or designed and certified for use in conjunction with oil-fired equipment;
(b) the appliances shall be located on the same storey;
(C) the vent outlet pressure of each appliance shall be negative;
(d) each appliance shall be equipped with an individual draft control, unless otherwise certified, so as to maintain the over-fire pressure (draft) specified by the appliance manufacturer;
(e) the vent connectors of the appliances shall be connected directly to a common vent connector of adequate cross-sectional area and as close to the chimney as practicable or directly to the chimney vent with the vent connector from the smallest appliance on top. A solid-fuel-fired appliance shall be connected below (upstream of) any oil-fired appliance connection;
(f) the chimney vent shall be capable of venting the flue gas by natural draft when all appliances are firing at the same time, or a mechanical flue-gas exhauster shall be used; and
(9) notwithstanding Item (e), an oil-fired appliance may be connected to a common vent serving two or more oil-only-fired appliances, in excess of the chimney vent capacity, provided that the appliances are equipped with a means to ensure that only the number of appliances the chimney is capable of venting (as determined in accordance with Clause 52.2.4) shall operate simultaneously at any time.
Note: Whentheventsoftwoor m oreappliancesareconnectedtoaslnglechim neyventviaacom m onventorm anifold, wye(Y’)oonnectionsofferlessresistancetoflue-gasflowthantee(r)connections.
When a chimney flue serving a liquid-fuelled appliance also serves a gas-fuelled appliance, the gas-fuelled
appliance vent connector shall be
(a) through a separate flue opening above the flue pipe connected to the liquid-fuelled appliance; or
(b) connected into a shop-fabricated branch fitting that is located
(i) in a dwelling unit not more than 750 mm (30 in) from the flue entrance; and (ii) in other than a dwelling unit, as close as practicable to the chimney.
When the total flue-gas temperature exceeds 400 °C (750°F), as determined in accordance with
Clause 22.214.171.124, the vent connector shall not pass through a combustible wall or partition.
When the total flue-gas temperature is 400 °C (750°F) or less, when determined in accordance with
Clause 6.2.1 .1, the vent connector may pass through combustible walls o partitions, provided that the
construction is guarded at the point of passage by one of the following means:
(a) a metal-ventilated thimble not less than 305 mm (12 in) larger in diameter than the pipe;
(b) a metal oi’ burned fire-clay thimble built in brickwork or other similar material extending not less than 203 mm (8 in) beyond all sides of the thimble; or
(C) in lieu of such protection as specified in Items (a) and (b), all combustible material in the wall or partition shall be cut away from the vent connector at a sufficient distance to provide the required clearance indicated in Table 4 and Figure 1 from such a vent connector. Any material used to close up such an oDeninci shall be noncombustible insulating material.CSA B139-09 pdf free download.
All resources on this website are from the Internet. It is only for personal study and research. No one is allowed to use it for any commercial purpose. If you need, please buy the genuine standard. If there is any infringement of your copyright, please contact the webmaster in time, and I will correct it immediately.
- Maybe you like
- Latest Updates
- ISO 287-2009 pdf free download
- ISO 527-5-2009 pdf free download
- ISO 659-2009 pdf free download
- ISO 660-2009 pdf free download
- ISO 712-2009 pdf free download
- ISO 725-2009 pdf free download
- ISO 730-2009 pdf free download
- ISO 927-2009 pdf free download
- ISO 2041-2009 pdf free download
- ISO 3040-2009 pdf free download
- ISO 3506-2-2009 pdf free download
- ISO 3506-3-2009 pdf free download