- Hot search：
CSA B52-05 pdf free download
CSA B52-05 pdf free download.Mechanical refrigeration code.
Condenser coil — a condenser constructed of pipe or tubing, other than a shell-and-tube or shell-and-coil type.
Condensing unit — a combination of one or more power-driven compressors, condensers, liquid receivers (when required), and regularly furnished accessories.
Container a cylinder for transporting refrigerant.
Critical pressure, critical temperature, and critical volume — a point on the saturation curve where the refrigerant liquid and vapour have identical volume, density, and enthalpy, and where there is no latent heat.
Critically charged system — a refrigeration system whose refrigerant charge is limited in such a way that it the entire charge is located in the evaporator(s), it is not possible for liquid refrigerant to be entrained in the compressor suction line.
Design pressure — the maximum allowable working pressure, expressed in kilopascals (pounds per square inch gauge) for which a specific part of a refrigeration system is designed.
Diffuser — a device used to dilute and disperse the discharge of a refrigerant gas.
Direct system — a system in which the evaporator or condenser of the refrigeration system is in direct contact with air or other substances to be cooled or heated.
Double direct system – a system in which an evaporative refrigerant is used in a secondary circuit to condense or cool a refrigerant in a primary Circuit. For the purposes of this Standard, each system enclosing a separate body of an evaporative refrigerant is considered a separate direct system.
Double Indirect open spray system — a system in which a secondary coolant that is cooled or heated by a refrigeration system is circulated to the air or other substance to be cooled or heated.
Duct — a tube or conduit used for the conveying or encasing purposes described in the following definitions:
Air duct — a tube or conduit used for conveying air.
Note: The air passages of seif-contaned sysems ore not considered to be ow ducts.
Pipe duct or tubing — a tube or conduit used for encasing pipe.
Evaporator — that part of a refrigeration system designed to produce refrigeration by vaporizing. Evaporator coil — an evaporator, constructed of pipe or tubing, that is not enclosed in a pressure vessel.
Exit — a confined passageway immediately adjacent to and including the door through which people leave a building.
Note: An exit can also be used for entering a building.CSA B52-05 pdf free download.
All resources on this website are from the Internet. It is only for personal study and research. No one is allowed to use it for any commercial purpose. If you need, please buy the genuine standard. If there is any infringement of your copyright, please contact the webmaster in time, and I will correct it immediately.
- Maybe you like
- Latest Updates
- ISO 287-2009 pdf free download
- ISO 527-5-2009 pdf free download
- ISO 659-2009 pdf free download
- ISO 660-2009 pdf free download
- ISO 712-2009 pdf free download
- ISO 725-2009 pdf free download
- ISO 730-2009 pdf free download
- ISO 927-2009 pdf free download
- ISO 2041-2009 pdf free download
- ISO 3040-2009 pdf free download
- ISO 3506-2-2009 pdf free download
- ISO 3506-3-2009 pdf free download