- Hot search：
CSA C49.8-09 pdf free download
CSA C49.8-09 pdf free download.Bare overhead aluminum conductors for distribution applications.
This CSA C49.8 specifies requirements for concentric-lay aluminum stranded conductors, with or without
a central core of reinforcing steel strand. These conductors are intended for overhead installation on
single-phase or three-phase electrical distribution systems.
In CSA Standards, “shall” is used to express a requirement, i.e., a provision that the user is obliged to satisfy in order to comply with the standard; “should” is used to express a recommendation or that which is advised but not required; “may” is used to express an option or that which is permissible within the limits of the standard; and “can” is used to express possibility or capability. Notes accompanying clauses do not include requirements or alternative requirements; the purpose of a note accompanying a clause is to separate from the text explanatory or informative material. Notes to tables and figures are considered part of the table or figure and may be written as requirements. Annexes are designated normative (mandatory) or informative (non-mandatory) to define their application.
The values given in SI units are the units of record for the purposes of this Standard. The values given in parentheses are for information and comparison only.
2 Reference publications
This Standard refers to the following publications, and where such reference is made, it shall be to the edition listed below, including all amendments published thereto.
CSA (Canadian Standards Association)
Zinc-coated steel wires for stranded conductors
CAN/CSA-C61 089-03 (R2008)
Round wire concentric lay overhead electrical stranded conductors
NEMA/EEMAC (National Electrical Manufacturers Association/Electrical Equipment
Manufacturers Association of Canada)
NEMA WC 26-2008/EEMAC 201-2008
Binational Wire and Cable Packaging Standard
3 Material and construction
Conductors listed in Table 1 shall meet the requirements of CAN/CSA-C61 089.
The steel core wire used for composite conductors listed in Table 1 shall meet or exceed the requirements for Si A wires specified in CAN/CSA-C60888, except for 3/0 AWG AACSR, which shall meet or exceed the requirements (or S3A wires.
Conductors shall be tested in accordance with CAN/CSA-C61 089.
4.2 Recoil and torque type test
The following test shall be performed for each strander set-up on A2 conductor 7-wire designs specified in
(a) At least 15 m of completed stranded conductor shall be pulled oft the strander, at the capstan, without allowing any rotation of the free conductor end. When the conductor is cut, the strands shall not unravel, and the conductor end shall not rotate more than two turns when released.
(b) The same conductor shall be laid out on a straight line. When the two ends are released, at least 60% of the length in the centre of the conductor shall be straight and shall not deviate from the line by more than 30 cm in either direction. The conductor shall lie flat with no veftical displacement.
5 Packaging and package marking
Completed conductors as specified in Table 1 shall be packaged on NEMA WC 26/EEMAC 201 Class Ill returnable wood reels or NEMA WC 26/EEMAC 201 Class I returnable steel fluted reels. Recommended metric shipping lengths are listed in Table Al.
The actual length on any reel shall fall within a tolerance of 5% of the shipping length specified for lengths of 1000 m or less, and within a tolerance of 3% for lengths greater than 1000 m.
A length of conductor shorter than that recommended in Table A.i may be supplied on a reel.
5.2 Package marking
Package marking shall be provided on one or more tags located on the outside of the reel flange. Where multiple tags are used, they shall be adjacent to each other.CSA C49.8-09 pdf free download.
All resources on this website are from the Internet. It is only for personal study and research. No one is allowed to use it for any commercial purpose. If you need, please buy the genuine standard. If there is any infringement of your copyright, please contact the webmaster in time, and I will correct it immediately.
- Maybe you like
- Latest Updates
- ISO 287-2009 pdf free download
- ISO 527-5-2009 pdf free download
- ISO 659-2009 pdf free download
- ISO 660-2009 pdf free download
- ISO 712-2009 pdf free download
- ISO 725-2009 pdf free download
- ISO 730-2009 pdf free download
- ISO 927-2009 pdf free download
- ISO 2041-2009 pdf free download
- ISO 3040-2009 pdf free download
- ISO 3506-2-2009 pdf free download
- ISO 3506-3-2009 pdf free download