- Hot search：
CSA N289.4-12 pdf free download
CSA N289.4-12 pdf free download.Testing procedures for seismic qualification of nuclear power plant structures, systems, and components.
220.127.116.11 Validation of dynamic characteristics
Where there are significant uncertainties in either the mathematical models or the dynamic phenomenon (e.g., effects of fluid pressure, non-linearity, etc.), testing shall be used to validate the dynamic parameters that are being used for analysis. Such verification usually includes the determination of natural frequencies, mode shapes, and damping values, although response level comparison may also be made.
Note: See Annex C toi more information on modal testing.
18.104.22.168 Testing by subassembly
Testing by subassembly may be applied where the SSC cannot be qualified by testing alone because of its size or complexity, or where a number of components are essentially the same, differing only in mass and in the location of internal components. For the purpose of this Standard, testing by subassembly means the application of analysis to determine the structural response characteristics at locations on a subassembly where components are to be mounted. The components are then seismically qualified by testing to seismic input motions determined by the analysis.
Note: An advantage of this method is that vanations in location and moss of subcomponents within a larger component can be assessed analytically once the analysis model is calibrated by test.
Testing of a multi-cabinet assembly is an example of the application of sub-assembly testing. It is usually impractical to test a multi-cabinet assembly of similar cabinets due to limitations in the size of testing facilities. The qualification of a single cabinet, or a few connected cabinets, may not be extrapolated to qualify a larger number of cabinets connected together in a lineup without adequate justification. This is because
(a) individual cabinets in the array may have different mass loading or mass distribution, or different structural stiffness, or both;
(b) the connected cabinets may exhibit different dynamic response, such as different torsional modes compared to the smaller number originally qualified; and
(C) the response of subcomponents mounted in different locations might be affected.
The approaches specified in Clause 9.3 of IEEE 344-04 may be used in conjunction with this Standard to justify the extrapolation of tests on a single cabinet, or a small number of connected cabinets, to qualify an assembly by analysis.
22.214.171.124 QualifIcation by similarity and interpolation
Different components varying only slightly in size and configuration, but being essentially identical in construction and dynamic behaviour, may be qualified by testing a representative item(s) and interpolating the test results to the remainder by analysis. This method can also be used to qualify an ensemble of a number of similar components by applying test results from an individual component or smaller assemblies of such components. The testing conducted on the typical component shall include determination of detailed dynamic parameters. CSA N289.4-12 pdf free download.
All resources on this website are from the Internet. It is only for personal study and research. No one is allowed to use it for any commercial purpose. If you need, please buy the genuine standard. If there is any infringement of your copyright, please contact the webmaster in time, and I will correct it immediately.
- Maybe you like
- Latest Updates
- ISO 287-2009 pdf free download
- ISO 527-5-2009 pdf free download
- ISO 659-2009 pdf free download
- ISO 660-2009 pdf free download
- ISO 712-2009 pdf free download
- ISO 725-2009 pdf free download
- ISO 730-2009 pdf free download
- ISO 927-2009 pdf free download
- ISO 2041-2009 pdf free download
- ISO 3040-2009 pdf free download
- ISO 3506-2-2009 pdf free download
- ISO 3506-3-2009 pdf free download