- Hot search：
IEC 63067-2020 pdf free download
IEC 63067-2020 pdf free download.Electrical installations for lighting and beaconing of aerodromes — Connecting devices — General requirements and tests
Installations électriques pour i’éclairageetle balisage des aérodromes — Dispositifs de connexion — Exigences generales et essais.
At the end of the soaking period, with the receptacle still immersed, apply a test voltage of 5 kV DC for 5 mm to Types II connecting devices and 15 kV DC to Type I connecting devices.
One minute after the test voltage has been applied the 500 V DC test is to be carried out between the conductors and water, and between conductors. The minimum insulation resistance between the conductors and water, and between conductors for both Type I and Type II connecting devices shall be 25 000 MO. The insulation resistance test shall be applied for minimum of 5 s or until the reading becomes stable.
NOTE Increasing of the values for minimum insulation resistance between the conductors and water, and between conductors are under consideration.
The receptacles having passed this test are now used for testing the corresponding plugs in a like test.
After these treatments, the specimens shall show no damage within the meaning of this document.
Compliance is checked by visual inspection.
15.3 Insulation resistance of connecting device assembly
After the conclusion of the test in 15.2, each plug and receptacle being tested shall be mated and immersed in a tap water bath the ambient temperature being 23 °C ± 3 °C.
Immerse 0,6 m of cable, 0,3 m ± 0,1 m of the plug, and 0,3 m ± 0,1 m of the receptacle. While immersed, each connecting device assembly shall be manually flexed for 2 mm and then left immersed for a minimum of 24 h with its cable leads flexed and maintained 1800±150 from its longitudinal axis.
Measure insulation resistance between conductors of each connected assembly after the 24 h soaking period. The resistance measurements shall be taken with a test voltage of 5 kV DC applied for 5 mm to Type II connecting devices and 15 kV DC to Type I connecting device.IEC 63067-2020 pdf free download.
All resources on this website are from the Internet. It is only for personal study and research. No one is allowed to use it for any commercial purpose. If you need, please buy the genuine standard. If there is any infringement of your copyright, please contact the webmaster in time, and I will correct it immediately.
- Maybe you like
- Latest Updates
- ISO 287-2009 pdf free download
- ISO 527-5-2009 pdf free download
- ISO 659-2009 pdf free download
- ISO 660-2009 pdf free download
- ISO 712-2009 pdf free download
- ISO 725-2009 pdf free download
- ISO 730-2009 pdf free download
- ISO 927-2009 pdf free download
- ISO 2041-2009 pdf free download
- ISO 3040-2009 pdf free download
- ISO 3506-2-2009 pdf free download
- ISO 3506-3-2009 pdf free download