- Hot search：
IEEE Std C37.20.1a-2020 pdf free download
IEEE Std C37.20.1a-2020 pdf free download.IEEE Standard for Metal-Enclosed Low-Voltage (1000 V ac and below, 3200 V dc and below) Power Circuit Breaker Switchgear Amendment 1: Control and Secondary Circuits and Devices, and All Wiring.
18.104.22.168 Control, secondary, and logic-level wiring
Flame-retardant, 600 V insulated stranded copper wire shall be used for internal wiring between components of switchgear assemblies, and to terminals for connection to external controls. metering, or instrumentation. Wiring within components is assumed to be covered by standards applicable to those devices and is not covered by this standard. Wiring for the purpose of conveying power to external switchgear loads is not covered by this clause.
The switchgear manufacturer is responsible for the performance of the wiring system provided by the manufacturer within the switchgear. This applies to the integrity of internally generated signals in the control wiring, and may require the use of special precautions such as shielded wire, twisted-pair wire, or segregation of certain wires.
For LV dc switchgear, wiring used to connect instrument. meters. and relays directly on circuits up to
3200 V, and any wiring connected directly to higher voltage circuits in LV dc switchgcar rated up to
3200 V, shall use wire rated for the maximum design voltage of the switchgear.
22.214.171.124.1 Wiring across a hinge
Wiring that crosses a hinge shall be suitable for this use, as defined by all of the following criteria:
a) Wire shall be sized according to 126.96.36.199.2.
b) Single conductors shall be stranded wire.
C) Wire shall be sufficiently flexible to withstand repeated door movement without sustaining damage to wire strands or insulation.
d) The loop formed by the wiring as it crosses the hinge shall be secured to the equipment at both ends. in such a manner that negligible strain is transmitted to wire beyond the securcments to prevent damage to the wire insulation as the door is moved.
c) Wiring shall not prevent the door from opening to the intended maximum opening. with a minimum opening of 90 degrees.IEEE Std C37.20.1a-2020 pdf free download.
All resources on this website are from the Internet. It is only for personal study and research. No one is allowed to use it for any commercial purpose. If you need, please buy the genuine standard. If there is any infringement of your copyright, please contact the webmaster in time, and I will correct it immediately.
- Maybe you like
- Latest Updates
- ISO 287-2009 pdf free download
- ISO 527-5-2009 pdf free download
- ISO 659-2009 pdf free download
- ISO 660-2009 pdf free download
- ISO 712-2009 pdf free download
- ISO 725-2009 pdf free download
- ISO 730-2009 pdf free download
- ISO 927-2009 pdf free download
- ISO 2041-2009 pdf free download
- ISO 3040-2009 pdf free download
- ISO 3506-2-2009 pdf free download
- ISO 3506-3-2009 pdf free download