- Hot search：
IEEE Std C37.20.2a-2020 pdf free download
IEEE Std C37.20.2a-2020 pdf free download.IEEE Standard for Metal-Clad Switchgear Amendment 1: Control and Secondary Circuits and Devices, and All Wiring.
b) All circuits supplied from internal sources (ac or dc) circuits shall have short-circuit protection
within the same section as the supply source. If these circuits are supplied by a control power
transformer, this protection may be in the primary circuit only.
c) Overcurrent protection of voltage circuits may be provided in addition to the required short-circuit protection.
d) Other circuits supplying loads, such as heaters, receptacles, and lights, shall have overload and short-circuit protection.
Overcurrent protection of current transformer secondary circuits shall not be provided. Open circuit protection should he considered where current transformer wiring connects to devices external to the switchgear assembly.
Primary and secondary protective devices may be omitted from voltage-dividing devices such as capacitive and resistive voltage dividers.
7.3.2 Voltage transformer fusing
The following requirements shall be met:
a) Primary circuits of all voltage transformers shall include current-limiting fuses.
b) Secondary circuits of all voltage transtbrmcrs shall include fuses or their equivalent.
EXCEPTION: Fuses may be omitted from secondary circuits of voltage transformers if the secondary burden includes voltage regulators. protective relays, or other devices considered sufficiently essential to the operation of the installation to make it preferable to incur the hazards associated with the possible destruction of the voltage transformer by a sustained secondary short-circuit rather than to risk interruption of the voltage supply to such devices as a result of a momentary secondary short-circuit.
7.3.3 Control, secondary, and logic-level wiring
Flame-retardant. 600 V insulated stranded copper wire shall be used for internal wiring between components of switchgear assemblies, and to terminals for connection to external controls, metering, or instrumentation. Wiring within components is assumed to be covered by standards applicable to those devices and is not covered by this standard. Wiring for the purpose of conveying power to external switchgcar loads is not covered by this clause.
The switchgear manufacturer is responsible for the performance of the wiring system provided by the manufacturer within the switchgear. This applies to the integrity of internally generated signals in the control wiring, and may require the use of special precautions such as shielded wire, twisted-pair wire, or segregation of certain wires.
126.96.36.199 Wiring across a hinge
Wiring that crosses a hinge shall bc suitable for this use, as defined by all of the following criteria:
a) Wire shall be sized according to 188.8.131.52.
b) Single conductors shall be stranded wire.IEEE Std C37.20.2a-2020 pdf free download.
All resources on this website are from the Internet. It is only for personal study and research. No one is allowed to use it for any commercial purpose. If you need, please buy the genuine standard. If there is any infringement of your copyright, please contact the webmaster in time, and I will correct it immediately.
- Maybe you like
- Latest Updates
- ISO 287-2009 pdf free download
- ISO 527-5-2009 pdf free download
- ISO 659-2009 pdf free download
- ISO 660-2009 pdf free download
- ISO 712-2009 pdf free download
- ISO 725-2009 pdf free download
- ISO 730-2009 pdf free download
- ISO 927-2009 pdf free download
- ISO 2041-2009 pdf free download
- ISO 3040-2009 pdf free download
- ISO 3506-2-2009 pdf free download
- ISO 3506-3-2009 pdf free download