- Hot search：
UL 83-2020 pdf free download
UL 83-2020 pdf free download.hermoplastic-Insulated Wires and Cables.
126.96.36.199 The nominal diameters of solid and stranded conductors are shown in Table 4 — Table 9. There are no diameter requirements for conductor classes not referenced in Tab!e4 — Table 9. See Clause 5.2 for conductor resistance requirements. The minimum diameter for stranded conductors is 98 percent of the nominal. The maximum diameter is 101 percent of the nominal. The diameter shall be determined in accordance with the test, Conductor diameter, in UL 2556, CSA C22.2 No. 2556, or NMX-J-066-ANCE.
4.1.6,2 Conductor sizes in mm2 (AWG/kcmil) covered by this Standard are shown in Table 4. The nominal cross-sectional area of a conductor identified in IIc4 is not a requirement.
188.8.131.52 A joint (butt splice) where allowed shall be made before or after insulating and prior to further processing. Where joints (butt splices) are made after insulating, the insulation applied over the joint shall be of the same insulation material used throughout the length of the conductor, or of another insulating material that meets or exceeds the electrical, physical, and mechanical requirements of this Standard for the original insulating material.
184.108.40.206 A joint in a solid conductor or in one of the individual wires of a stranded conductor shall neither increase the diameter nor materially decrease the strength of the conductor or the individual wire. Not more than one of the wires in a stranded conductor of 19 wires or less, nor more than one of the wires in any given layer in a stranded conductor of more than 19 wires, shall be joined in any 0.3 m (1 ft) of conductor.
220.127.116.11 In a rope-lay-stranded conductor, wtiicli consists of a central core surrounded by one or more layers of stranded members (primary groups), each member shall be considered equivalent to a solid wire, and as such, shall be spliced as a unit. These joints shall not be any closer together than 2 lay lengths.
18.104.22.168 A joint shall be allowed in a Class B stranded 2.08 mm2 (14 AWG), 3.31 mm2 (12 AWG), 5.26 mm2 (10 AWG), or 8,37 mm2 (8 AWG) insulated copper conductor intended to be used in a multiple- conductor cable, with an overall covering. The joint (butt splice) shall be made by machine brazing or welding the entire conductor such that the resulting solid section of the stranded conductor is no ‘onger than 13 mm (0.50 inch). In addition, the joint shall not increase the diameter of the conductor, there shall be no sharp points, and the distance between joints in a single conductor shall not average less than 1000 m (3280 ft) in any finished length of that single insulated conductor. Insulated conductors with a joint (butt splice) shall not be surface marked with a type designation.
A separator of suitable material between the conductor and the insulation shall be optional. The separator shall be of contrasting color to the conductor color, except that clear or green shall not be used. Whitecolored separator over aluminum conductors shall be optional. The separator and the other wire or cable components shall not have any deleterious effect on each other.UL 83-2020 pdf free download.
All resources on this website are from the Internet. It is only for personal study and research. No one is allowed to use it for any commercial purpose. If you need, please buy the genuine standard. If there is any infringement of your copyright, please contact the webmaster in time, and I will correct it immediately.
- Maybe you like
- Latest Updates
- ISO 287-2009 pdf free download
- ISO 527-5-2009 pdf free download
- ISO 659-2009 pdf free download
- ISO 660-2009 pdf free download
- ISO 712-2009 pdf free download
- ISO 725-2009 pdf free download
- ISO 730-2009 pdf free download
- ISO 927-2009 pdf free download
- ISO 2041-2009 pdf free download
- ISO 3040-2009 pdf free download
- ISO 3506-2-2009 pdf free download
- ISO 3506-3-2009 pdf free download