- Hot search：
UL 83-2020 pdf free download
UL 83-2020 pdf free download.Thermoplastic-Insulated Wires and Cables.
This test shall not be required on insulated conductors that meet the requirements of Clause 5.5.
5.6.2 Acceptance criteria
22.214.171.124 The 90 C rated insulation of the individual conductors without covenng shall have insulation resistance in air at 97 ±1’C that is not less than specified in Table 25 at any time during an extended period in an acceptable full-draft circulating-air oven. The period in the oven shall be 12 weeks or more, if the insulation resistance throughout the last 6 weeks of the initial 12-week period in the oven is greater than 3 GUm (10 MO 1000 ft). The period in the oven shall be at least 24 weeks and no more than 36 weeks, unless requested by the manufacturer if the insulation resistance is less than 3 GO-rn (10 MO-bOO ft) at any point during the last 6 weeks of the initial 12-week period in the oven, but equals or exceeds the value specified in Table 25. An a-c voltage equal to the voltage rating of the wire (600 V mis) shall be applied to the insulated conductor at all times other than while measuring the insulation resistance. In the case of nylon-jacketed wires, the nylon shall be removed prior to testing. These tests are accelerated tests. The values in Table 25 apply only to conductor types with the corresponding insulation thicknesses specified in this Standard.
126.96.36.199 The insulation resistance shall be measured between the conductor and an electrode consisting of either graphite powder, a snug-fitting close-weave copper braid of minimum 90 percent coverage applied over the insulation, or other equivalent means.
188.8.131.52 The maximum weekly decrease in insulation resistance as determined in Clause 184.108.40.206 shall not be more than 4 percent if the insulation resistance throughout the last 6 weeks of the period in the oven is 3 GO-rn (10 MO-bOO ft) or more, and shall not be more than 2 percent if the insulation resistance at any point during the last 6 weeks of the initial 12-week period in the oven is less than 3 GO-rn (10 MO-bOO ft). but more than the values specified in Table 25. If the results of the test do not meet either of these criteria. but are more than the values specified in Table 25. the period of immersion may be extended by one week intervals at the request of the manufacturer, subject to the minimum test period established in ,.53. If the insulation resistance faIls below the values specified in Table 25, the test shall be discontinued and considered a failure.
5.6.2 4 The maximum weekly decrease in insulation resistance shall be calculated as the slope of a least squares best fit straight line curve drawn through a three-week moving average of the last six weeks of raw test data. Each three-week moving average data point for the least squares best fit straight line curve shall be calculated as the average of the raw data for the current week and the previous two weeks (for example. the week 12 data point would be the average of the weeks 10. 11 and 12 raw data values).
220.127.116.11 Compliance with 18.104.22.168 — 22.214.171.124 shall be determined in accordance with the test, Long-term insulation resistance (Method 2). in UL 2556. CSA C22.2 No. 2556. or NMX-J-556-ANCE.UL 83-2020 pdf free download.
All resources on this website are from the Internet. It is only for personal study and research. No one is allowed to use it for any commercial purpose. If you need, please buy the genuine standard. If there is any infringement of your copyright, please contact the webmaster in time, and I will correct it immediately.
- Maybe you like
- Latest Updates
- ISO 287-2009 pdf free download
- ISO 527-5-2009 pdf free download
- ISO 659-2009 pdf free download
- ISO 660-2009 pdf free download
- ISO 712-2009 pdf free download
- ISO 725-2009 pdf free download
- ISO 730-2009 pdf free download
- ISO 927-2009 pdf free download
- ISO 2041-2009 pdf free download
- ISO 3040-2009 pdf free download
- ISO 3506-2-2009 pdf free download
- ISO 3506-3-2009 pdf free download