- Hot search：
AS 1668.1-2015 pdf free download
AS 1668.1-2015 pdf free download.The use of ventilation and air conditioning in buildings Part 1: Fire and smoke control in buildings.
Concessions shall apply for the omission of fire dampers for openings that are—
(a) located in an external clement where an unprotected opening is permitted by building regulations;
(b) located in a toadbearing element required to have an FRL with respect to structural adequacy only;
(C) protected with enclosing construction in accordance with Clause 3.4:
(d) protected by Construction equivalent to a prototype test specimen in accordance with Clause 3.5;
(e) contained in a shaft such that the required level of tire separation is maintained (see Figure 3.1), or
(I’) located at the entry to a shaft where the FRL of the shaft is maintained through all other fire compartments traversed by that shaft (see Figure 3.1).
For the purposes of Items (e) and (1), shafts shall not form part of multiple fire compartments simultaneously.
Openings in building elements that are required to have an FRL shall not include fire dampers, and shall be protected by other means where such openings are—
(a) associated with a system that is protected with subducts in accordance with Clauses 3.6 and 3.7.4;
(b) associated with a duct forming part of a kitchen exhaust system required to comply with AS 1668.2. which shall be installed in accordance with Section 6:
(c) associated with a duct forming part of a common residential kitchen exhaust system that is configured as a minor exhaust system and provided with subducts in accordance with Clauses 3.6 and 3.7.4;
(d) part of a lift %crn. which shall be configured in accordance with Clause 3,4;
(e) associated with a diesel tire pump room ventilation system, which shall be configured in accordance with Clause 3.4;
(0 associated with a dedicated tire-isolated cxit pressuriiation system, which shall be configured in accordance with Section 10: and
(g) associated with a fume cupboard exhaust system where—
(I) accelerated corrosion of the tire damper resulting in failure in less than 5 years;
(ii) exposure of maintenance personnel to toxic substances during inspection; or (iii) exposure of laboratory staff to toxic substances in the event of faulty tire
cannot be avoided, in which case the system shall be configured in accordance with Clause 3.4.AS 1668.1-2015 pdf free download.
All resources on this website are from the Internet. It is only for personal study and research. No one is allowed to use it for any commercial purpose. If you need, please buy the genuine standard. If there is any infringement of your copyright, please contact the webmaster in time, and I will correct it immediately.
- Maybe you like
- Latest Updates
- ISO 287-2009 pdf free download
- ISO 527-5-2009 pdf free download
- ISO 659-2009 pdf free download
- ISO 660-2009 pdf free download
- ISO 712-2009 pdf free download
- ISO 725-2009 pdf free download
- ISO 730-2009 pdf free download
- ISO 927-2009 pdf free download
- ISO 2041-2009 pdf free download
- ISO 3040-2009 pdf free download
- ISO 3506-2-2009 pdf free download
- ISO 3506-3-2009 pdf free download