- Hot search：
AS 4643-2007 pdf free download
AS 4643-2007 pdf free download.Overhead radiant tube gas heaters.
826 M.O.T. 5.9.1 – 85 HEAT RESISTANCE
This test applies to all appliances.
The appliance is operated continuously for 100 cycles of 2 h on and I h off at overload gas consumption and then checked for any deterioration.
I Equipment as set out in Clause 3.2.6.
2 Suitable timing device.
Supply of appropriate test gas (see Clause 3.1.2) at a pressure to give overload gas consumption.
826.5 PREPARATION OF APPARATUS
I Install the appliance as set out in Clause 3.2.
2 Examine the appliance and ensure that it does not ha’e any structural. mechanical or operational defects.
I Light burner and adjust to overload gas consuniption within 2 mm from cold condition.
2 Operate for 100 cycles of 2 h on and I h off. Any thermostats shall bc set at maximum.
3 Turn off gas.
4 Disconnect and examine the appliance.
The appliance complies with this requirement provided:
(a) Doors and other movable fittings function correctly.
(b) Outer surface finishes of the appliance have not deteriorated.
(C) Controls, thermostats etc. do not leak, seize or fail.
(d) The appliance does not slio signs of deterioration (superficial discolouration shall be ignored).
(e) Burners hae not distorted or deteriorated sufficiently to affect normal operation.
(f) Motors and fans have not deteriorated.
(g) Wiring insulation has not scorched or melted.
B27 M.O.T. 5.9.2—85 hEAT RESISTANCE — LIT BACK CONDITION
[his test applies to all appliance burners in which a lit back condition can be established.
Each burner is tested to establish if it can be operated in the lit hack condition.
If a lit back condition can be established, the burner is allowed to operate in this condition for I h at the maximum gas rate at which the lit back condition can be maintained.
I Equipment as specified in Clause 3.2.6.
2 Suitable liming device.AS 4643-2007 pdf free download.
All resources on this website are from the Internet. It is only for personal study and research. No one is allowed to use it for any commercial purpose. If you need, please buy the genuine standard. If there is any infringement of your copyright, please contact the webmaster in time, and I will correct it immediately.
- Maybe you like
- Latest Updates
- ISO 287-2009 pdf free download
- ISO 527-5-2009 pdf free download
- ISO 659-2009 pdf free download
- ISO 660-2009 pdf free download
- ISO 712-2009 pdf free download
- ISO 725-2009 pdf free download
- ISO 730-2009 pdf free download
- ISO 927-2009 pdf free download
- ISO 2041-2009 pdf free download
- ISO 3040-2009 pdf free download
- ISO 3506-2-2009 pdf free download
- ISO 3506-3-2009 pdf free download